PUFP CT DB: Two 20A GFCI protected Pop Up Power Outlets
The PUFP-CT-DB by Lew Electric is a pop up power box designed to be installed in a countertop surface in dry or wet locations, they are ideal for kitchen islands, bars, restaurants, hotels, or anywhere that you need a kitchen certified power pop up. The top features a dark bronze finish and creates a beautiful contrasting look to any kitchen that has stainless steel appliances. When you need access to your power simply push the button and your power pops up ready for you to plug into the outlets, when you are done press it shut till it closes. The power outlet is a decora 20 amp receptacle that is GFCI protected and features tamper resistant outlets, to install the outlet must be hardwired as it does not come with a corded plug.
The pop up is IP44 rated for wet applications and is also splash rated. On the underside of the bezel there is a waterproof gasket that keeps water from entering from your countertop. The pop up only takes up 3 1/8" of space under your counter so it can be installed in almost any location. Use a pop up in a counter for quick access to power when a wall outlet is not possible and to keep dangerous cords hanging from kitchen counters.
Installation is easy, to install cut your 4 1/16" x 4 1/16" hole in your countertop. From the underside of your counter install the included back box with construction adhesive for granite or quartz, and wood screws for a Formica or wood countertop. When installed run your wire into the rear knockout of the back box and connect your bare wires to the terminal block on the pop up, when finished push as much wire out from the box and the remaining push flat in the bottom of the box. Next, pop open the unit and with the provided 2 screws secure to the back box. Lastly, test the opening speed of the unit by pressing the button and holding till it pops up, to close press the button and push till it latches shut. If the opening speed needs to be adjusted use a Phillips screwdriver to adjust the speed of the pop up.
Splash Proof, IP44 Rated, ETL Listed, and Complies with NEC Code 406.5E for use in Countertops
The PUFP-CT-DB passes electrical code for kitchen use in a variety of ways. First, it features a self testing GFCI compliant 20 amp two power hardwired outlet. Second, the two plugs feature tamper resistant outlets. Third, the outlet is a UL listed receptacle #E60120 and conforms to UL code 514A and 498. Fourth, the entire unit is ETL and cETL listed to code 3176286 and complies with NEC code 406.5E for countertop use in the USA and Canada.
Dimensions and Certifications
ETL listed for the USA and Canada
Complies with NEC code 406.5(E) for use in countertops
Bezel dimensions: 4 7/8" X 4 11/16"
Cutout dimensions: 4 1/16" x 4 1/16" ***It is recommended to have the product in hand before cutting***
Space Needed Below Counter: 3.13"
Counter thickness: 1/2" to 2"
Back box dimensions: 3 15/16" x 4"
Includes back box shown in picture
Two 20A GFI power outlets
Tamper resistant outlets
Waterproof gasket under bezel
Warranty: 1 Year